- Initial inspection revealed power and ground to compressor but compressor is not engaging.. Performed evac/recharge and found that system was empty of refrigerant. Recharged system to proper 1.1 lbs with adding UV dye. Found no visible signs of leak at this time at compressor, service ports, hoses or drain tube. System is now blowing at 45 degrees. If system begins to blow warm in the future, customer will need to return for further inspection.
- AC evacuation and recharge system, UV dye, and refrigerant
Jack R. gave our service a 5 star review on 3/1/2023